TOLL GATE SEWER REPAIR
AT A GLANCE
• Brick and Concrete Manholes
• Sewer Structures
• Scheduled Shutdowns
In Warwick, Rhode Island, the public school district identified a need to rehabilitate 13 concrete and brick sewer structures. The critical challenge was maintaining operations while being repaired.
With Warren Environmental’s 100% solids epoxy coating system specified, A&W Coatings was awarded the job. To keep the manholes operational, A&W internally bypassed the system utilizing flow-through plugs and was able to work in live-flow conditions. After the team prepared the surfaces through high-pressure water blasting, they coated the structures with a minimum of 250 mils of epoxy, with some requiring as much as 375 mils based on the deterioration. All interior surfaces were coated, including the bench and the invert.
The project was completed in April 2019 and was inspected a year later. The inspection team pressure-washed the structures and then performed multiple pull tests. All the manholes were in great condition, with pull test results ranging from 730 to 1,422 psi.